Common installation practise for telecom equipment installed in ETSI- or 19"- racks, are that two power buses (A and B) are connected to the top of the rack. Within the rack this is distributed to each panel/sub-rack on separate buses.
The fuse distribution panel MP209 may be mounted in any type of ETSI- and 19”-rack and gives 48 Vdc distribution for max 32A fuses and up to 35mm2 cables.
By turning the mounting brackets the panel may be mounted in both ETSI- and 19"- racks. The brackets may also be set in the back of the panel for mounting on a wall or to the back-profiles in deep racks.
All inn- and outgoing power cables enters from the top through the rubber glands, and are secured with tie-wraps.
To avoid a mix of fuse elements and terminal blocks, two-pole fuses are used. Only the negative side has an active fuse element, but both sides will break when triggered. A fuse element may be changed without breaking the other fuses.
Specification Dimensions (H x B x D): 230 x 484 (19”) x 100 mm May be converted to metric